## (4)  Star-Delta Connection:

• In this type of connection, then primary is connected in star fashion while the secondary is connected in delta fashion as shown in the Fig.

• The voltages on primary and secondary sides can be represented on the phasor diagram as shown in the Fig.

## Key point:

• As Primary in Star connected
• Line voltage on Primary side = √3 X Phase voltage on Primary side. So
• Phase voltage on Primary side = Line voltage on Primary side / √3
• Now Transformation Ration (K) = Secondary Phase Voltage / Primary Phase Voltage
• Secondary Phase Voltage = K X Primary Phase Voltage.
• As Secondary  in delta connected:
• Line voltage on Secondary side = Phase voltage on Secondary side.
• Secondary Phase Voltage = K X Primary Phase Voltage. =K X (Line voltage on Primary side / √3)
• Secondary Phase Voltage = (K/√3 ) X Line voltage on Primary side.
• There is s +30 Degree or -30 Degree Phase Shift between Secondary Phase Voltage to Primary Phase Voltage

## Advantages of Star Delta Connection:

• The primary side is star connected. Hence fewer numbers of turns are required. This makes the connection economical for large high voltage step down power transformers.
• The neutral available on the primary can be earthed to avoid distortion.
• The neutral point allows both types of loads (single phase or three phases) to be met.
• Large unbalanced loads can be handled satisfactory.
• The Y-D connection has no problem with third harmonic components due to circulating currents inD. It is also more stable to unbalanced loads since the D partially redistributes any imbalance that occurs.
• The delta connected winding carries third harmonic current due to which potential of neutral point is stabilized. Some saving in cost of insulation is achieved if HV side is star connected. But in practice the HV side is normally connected in delta so that the three phase loads like motors and single phase loads like lighting loads can be supplied by LV side using three phase four wire system.
• As Grounding Transformer: In Power System Mostly grounded Y- ∆ transformer is used for no other purpose than to provide a good ground source in ungrounded Delta system. Take, for example, a distribution system supplied by  connected (i.e., un-grounded) power source. If it is required to connect phase-to-ground loads to this system a grounding bank is connected to the system, as shown in Figure

• This system a grounding bank is connected to the system, as shown in Figure. Note that the connected winding is not connected to any external circuit in Figure.
• With a load current equal to 3 times i, each phase of the grounded Y winding provides the same current i, with the  -connected secondary winding of the grounding bank providing the ampere-turns required to cancel the ampere-turns of the primary winding. Note that the grounding bank does not supply any real power to the load; it is there merely to provide a ground path. All the power required by the load is supplied by two phases of the ungrounded supply